High transfer resistance can be identified by measuring static contact resistance. Dynamic contact resistance measurements can be used to determine the resistance characteristic during a freely definable switching operation.
Testing with earthing on both sides
Switchgear equipment is often tested with earthing on both sides in order to prevent danger caused by capacitively coupled voltages from neighbouring components. When tests are carried out in combination with PROMET SE, measurements can be carried out with earthing on both sides.
Integrated operating and evaluation unit
The resistive 7“ touch screen, a new operating concept and extra powerful hardware make for easy operation and optimum display of all information.
Using the integrated control panel of ACTAS P260 | P360, it is possible to carry out complete tests on medium-, high- and extra-high-voltage switchgear.